for Powell, OH
Replace Out of Warranty Part on A/C unit. Replaced evap coil. System held nitrogen test, no leaks. Compressor currently faulty. system turns on pressures 45/325 system will shut down on low pressure and cycle back on. Pressures 200/200 compressor has bad valves or bad pressure relief valve. Both components are not repairable. Compressor needs changed, under warranty
Performing a Carrier pre-season maintenance on furnace.